Water Conditioner Filtersorb SP3 Scale Removal TAC Media. 15 GPM.
SALT FREE WATER CONDITIONER. 15 GPM WHOLE HOUSE SYSTEM
NO Salt Water Conditioning
Scale Prevention System (New Technology)
Some important points are mentioned here about the credibility of the media
• No TDS change: As FILTERSORB® SP3 , does not take out or give in anything in the water. As no ion-exchange chemistry is used the TDS of the water remains unchanged before and after the treatment
• No pH change: pH of the water remains same. This factor makes the treated water suitable for almost any use where corrosion is concerned
• Rich Minerals Preserved: FILTERSORB® SP3 does not add up sodium or any chemicals in the water. It simply preserves the Calcium and Magnesium contents of water, making the treated water the healthiest mineral water available. These Calcium and Magnesium are quintessential for nervous systems & muscles functionalities. They are indispensible parts in the cell chemistry of the plants and most of the life forms on earth
• De-Scaling: Not only FILTERSORB® SP3 prevents scale formation in water channels, but it also helps to reduce the previously formed scales. The NAC process takes out water dissolved CO2 in almost-visible micro-bubbles forms that helps reducing previously formed scale over a period of time (depends on the usage period).
NO lime scale build-up on pipes, fixtures or appliances and can even remove existing scale in some cases!
Easy Installation, Two Connections, Simple pipe in /pipe out!
Saves water no backwash required simple flow through to point of use!
NO power required NO timer or backwash cycle!
NO chemicals or salt required!
NO maintenance! NO drain required!
Will not harm the environment; adds or removes nothing from the water while giving the benefits of soft water!
Saves energy by eliminating the need to heat through insulating scale and save money by extending the life of pipes and appliances!
The essential calcium and magnesium nutrients removed by traditional water softeners remain and there is no sodium added as with traditional softeners to aggravate cardiovascular or other health problems.
Fits in limited space one small tank no brine tanks or large regeneration tanks!
How It Works
Calcium ions, magnesium ions and bicarbonate ions in untreated water form scale on the inside walls of pipe, exterior of fixtures and on heating surfaces because crystallization is not taking effect efficiently between the ions due to their suspension between water molecules and the need to come together in the proper alignment to form crystals. Therefore they form as scale on the surfaces of the water system.
The system is a simple “physical water treatment” known as TAC (Template Assisted Crystallization) Template=mold, guide or pattern. Assisted=Help or make easy. Crystallization=Form a definite shape.
Inside the TAC treatment tank are porcelain beads with the atomic level pattern of the crystal etched on their surface allowing for the calcium, magnesium and bicarbonate ions to come together on the template to created millions of microscopic crystals of scale that rapidly form and are released from the bead immediately into the treated water, not forming on the contact surfaces of the water system and are carried downstream in suspension through the water system.
The crystal formation on the microscopic crystals (seed crystals) created on the beads and released in the water stream are the lowest energy reaction possible between the ions therefore existing scale will be dissolved back into the water stream by reacting with and forming crystals.
The seed crystals are constantly being formed on the beads and released as catalyst for crystal growth in the water steam.
Crystallization is the process that the “magnet process” and “electrical charging of water” claim to achieve. But by independent testing the electrical and magnetic methods are a maximum of 60% effective at scale prevention leaving an unacceptable level of 40% scaling. The TAC method is tested at 99.9% efficient at scale prevention and removal.
Chlorine in the water supply will degrade it if not treated. Since most water supply is chlorinated, we highly recommend the carbon filter to precede the unit.
◦ FRP Tank (Color Varies)
◦ Clack upflow Valve
◦ By Pass Valve
◦ 1" Pipe Adapter Kit
◦ Filtersorb SP3 media
Water Chemistry & Limitations:
pH 6.5 to 9.5
Hardness Max 75 Grains (1400 ppm CaCO3)
Temperature 41 to 140 F (5-60 C)
Chlorine <3 ppm
Iron 0.5 mg/l
Manganese 0.05 mg/l
Copper 1.3 mg/l
Oil & H2S Remove prior to Scalestop
Polyphosphates Remove prior to Scalestop
Recommended operating temp.(°C)5 to 90pH range 6.5 to 9.5Hardness (carbonate), max. ppm 1400 Salinity, max. ppm 35000. Iron, max. ppm 0.5. *Manganese, max. ppm 0.05. Free chlorine, max. ppm3. Copper, max. ppm1.3 Oil Free Hydrogen sulfide Free.
Most items ships within 1 business day of completed payment.
Used or installed items are not eligible for return, returned items must be in original unused condition..